0
Research Papers

# Effects of Decay Heat Distribution on Water Temperature in a Spent Fuel Pit and Prediction Errors With a One-Region Model

[+] Author and Article Information
Chihiro Yanagi

Institute of Nuclear Safety System, Inc.,
64 Sata, Mihama-cho, Mikata-gun, Fukui 919-1205, Japan
e-mail: yanagi.chihiro@inss.co.jp

Michio Murase

Mem. ASME
Institute of Nuclear Safety System, Inc.,
64 Sata, Mihama-cho, Mikata-gun, Fukui 919-1205, Japan
e-mail: murase@inss.co.jp

Yoichi Utanohara

Institute of Nuclear Safety System, Inc.,
64 Sata, Mihama-cho, Mikata-gun, Fukui 919-1205, Japan
e-mail: utanohara@inss.co.jp

1Corresponding author.

Manuscript received June 9, 2015; final manuscript received January 5, 2016; published online June 17, 2016. Assoc. Editor: Emmanuel Porcheron.

ASME J of Nuclear Rad Sci 2(3), 031001 (Jun 17, 2016) (10 pages) Paper No: NERS-15-1113; doi: 10.1115/1.4032507 History: Received June 09, 2015; Accepted January 06, 2016

## Abstract

A prediction system with a one-region (1R) model was developed to predict water temperature in a spent fuel pit (SFP) after the shutdown of its cooling systems based on three-dimensional (3D) thermal-hydraulic behavior computed by using the computational fluid dynamics (CFD) software, FLUENT 6.3.26. The system was later extended to compute the water level in the SFP during the loss of all AC power supplies. This study aimed at confirming the applicability of the 1R model by the comparison of 3D computation results and 1R calculation results. Some of the effects that influence the SFP water temperature increase are decay heat and its distribution. Also, decay heat decreases with time, so for low decay heat, natural circulation force in the SFP becomes weak and the effect of heat loss to air for the water temperature increase will be relatively bigger than that for high decay heat. Therefore, in this study, the 3D computations with FLUENT 15.0 were done for four typical patterns of decay heat distribution and for three decay heat values (10, 5, and 1-MW). The computational results were compared to each other and evaluated. It was found that the effects of decay heat distribution were small on water temperature calculations, and the 1R model for SFP water was applicable to the prediction of SFP water temperature during the loss of all AC power supplies without consideration of the decay heat distribution.

<>

## References

Wang, J. R., Lin, H. T., Wang, T. C., Chen, H. C., Yang, J. H., and Shih, C., 2014, “MELCOR/SNAP Analysis of Chinshan (BWR/4) Nuclear Power Plant Spent Fuel Pool for the Similar Fukushima Accident,” The 10th International Topical Meeting on Nuclear Thermal-Hydraulics, Operation and Safety (NUTHOS-10), , Atomic Energy Society of Japan, Tokyo, Japan.
Zhang, Z., and Liang, T. K. S., 2014, “Analysis of the Loss of Cooling Accident for the Spent Fuel Pool of Nuclear Power Plant Using MELCOR,” The 10th International Topical Meeting on Nuclear Thermal-Hydraulics, Operation and Safety (NUTHOS-10), , Atomic Energy Society of Japan, Tokyo, Japan.
Yanagi, C., Murase, M., Yoshida, Y., Iwaki, T., Nagae, T., and Koizumi, Y., 2012, “Evaporation Heat Flux From Hot Water to Air Flow,” Trans. Jpn. Soc. Mech. Eng. B, 78(786), pp. 363–372 (in Japanese).
Yanagi, C., Murase, M., Yoshida, Y., Iwaki, T., and Nagae, T., 2012, “Evaluation of Heat Loss and Water Temperature in a Spent Fuel Pit,” J. Power Energy Syst., 6(2), pp. 51–62.
Yanagi, C., Murase, M., Yoshida, Y., Utanohara, Y., Iwaki, T., and Nagae, T., 2012, “Numerical Simulation of Water Temperature in a Spent Fuel Pit During the Shutdown of Its Cooling Systems,” J. Power Energy Syst., 6(3), pp. 423–434.
Fluent Inc., 2003, FLUENT 6 User’s Guide, Fluent Inc., Tokyo, Japan.
Yanagi, C., Murase, M., Yoshida, Y., and Kusunoki, T., 2015, “Prediction of Temperature and Water Level in a Spent Fuel Pit During Loss of All AC Power Supplies,” J. Nucl. Sci. Technol., 52(2), pp. 193–203.
Yanagi, C., and Murase, M., 2013, “One-Region Model Predicting Water Temperature and Level in a Spent Fuel Pit During Loss of All AC Power Supplies,” J. Power Energy Syst., 7(1), pp. 18–31.
Hung, T. C., Dhir, V. K., Pei, B. S., Chen, Y. S., and Tsai, F. P., 2013, “The Development of a Three-Dimensional Transient CFD Model for Predicting Cooling Ability of Spent Fuel Pools,” Appl. Therm. Eng., 50(1), pp. 496–504. 1359-4311
ANSYS Inc., 2013, ANSYS FLUENT 15 User’s Guide, ANSYS Inc., Tokyo, Japan.
Kataoka, Y., Fujii, T., Murase, M., and Tominaga, K., 1994, “Experimental Study on Heat Removal Characteristics for Water Wall Type Passive Containment Cooling System,” J. Nucl. Sci. Technol., 31(10), pp. 1043–1052.
Takamori, K., Fujii, T., Kataoka, Y., and Murase, M., 1994, “Experimental Analysis on Mitigation of Thermal Stratification in the Suppression Pool of a Water Wall Type Passive Containment Cooling System,” J. Nucl. Sci. Technol., 31(7), pp. 735–744.

## Figures

Fig. 1

1R model during the loss of all AC power supplies [8]

Fig. 2

Computational grid for computations of thermal hydraulics in the SFP [4]. (a) Outer surface of computational grid. (b) Computational grid of racks

Fig. 3

(a) Initial conditions for velocity distribution (Y=0.45  m, 5-MW, uniform). (b) Initial conditions for temperature distribution (Y=5  m, 5-MW, uniform)

Fig. 4

(a) Effect of the decay heat on water temperature [5]. (b) Effect of the decay heat on heat loss to air [5]

Fig. 5

(a) Heat loss to air (10-MW). (b) Heat loss to air (5-MW). (c) Heat loss to air (1-MW)

Fig. 6

(a) Measuring-point temperature (10-MW). (b) Measuring-point temperature (5-MW). (c) Measuring-point temperature (1-MW)

Fig. 7

Effects of mesh sizes (cf. Fig 6(a) for the values of measuring-point temperature)

Fig. 8

Effects of time steps

Fig. 9

(a) Effects of turbulence models (10-MW). (b) Effects of turbulence models (1-MW)

## Errata

Some tools below are only available to our subscribers or users with an online account.

### Related Content

Customize your page view by dragging and repositioning the boxes below.

Related Journal Articles
Related Proceedings Articles
Related eBook Content
Topic Collections